Air Conditioner not Running(New Run Capacitor 70+7,5 mF x 440V) – in San Jose, CA
Customer: “Our 14-year-old A/C unit stopped running altogether tonight. It’s been struggling to blow cold air throughout our townhouse for quite some time– it will run continuously for 2 hours while only bringing the room temp down from 80 to 78. We’d like to get it fixed ASAP before the next heat wave hits.”
Air Conditioner not Running/Replacement Of Run Capacitor
1. Old Run Capacitor failed, was replaced for new.
2. Too low refrigerant level in system did not give enough low temperature and was 78 Fahrenheit. Two pounds of refrigerated has been added. And the temperature at the exit of the registers reached 59.7 Fahrenheit.
Сonditioner refilling with refrigarant